E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic Terminal block. E5CN. Basic Type. Analog input. Temperature input. safety standards, refer to your OMRON website. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type (Cat. No. H). E5CN-H. Advanced Digital Temperature Controller (48 x 48 mm). E5CN-H between displaying the status of the Temperature Controller (auto/manual.
|Published (Last):||14 December 2004|
|PDF File Size:||10.19 Mb|
|ePub File Size:||13.23 Mb|
|Price:||Free* [*Free Regsitration Required]|
Section Performing Manual Control 7. Connect the power supply. Use the U okron to set the parameter to Page al1n Alarm 1 Open in Alarm Alarm 1 must be assigned. Page of Go. Page Standby sequence reset: Press the U key to set the parameter to r-gr. Section Using the Support Software Port 3.
Control output heating ; Control output 2: PageAlarm 3 hysteresis: Section Performing Manual Control Operating Procedure Use the following procedure to set the manipulated variable in manual mode.
Move to the advanced function setting level. Page Section Loop Break Alarm 3. Page initial setting levelST stable range advance function setting level: A functional explanation is provided here for illustration, but models are not necessarily available for all possible combinations.
Page 5 Performance data given in this manual is provided as a guide for the user in determining suitability and does not ee5cn a warranty.
Heater Burnout Latch Alarm 1 must be assigned. Other Functions Improved visibility A 7-segment digital display also possible. PageAlarm 1 hysteresis: Press the O key for at least three seconds to move from the operation Operation Level level to the initial setting level. Section Using the Simple Program Function Starting Method Any of the following three methods can be used to start the simple program.
Precautions for Safe Use Be sure to observe the following precautions e5n prevent operation failure, malfunction, or adverse affects on the performance and functions of the product.
OMRON E5CN USER MANUAL Pdf Download.
Conventions Used in this Section Set point upper- sl-h limit 3. Page Soak time, Wait band adjustment level: Press the O and M keys simultaneously for at least one second to return Operation Level to the operation level.
Moreover, because OMRON is con- stantly striving to improve its high-quality products, the information contained in this manual is subject to change without notice. Change the connections as follows: When the M key is pressed, the status changes as shown to the left. Initial setting level To limit the SP setting When the manipulated variable turns OFF, the temperature begins to fall and the control turns ON again. Calibrating Analog Input analog Input 1,2, The set point limiter is used to prevent the control target from reaching abnormal tem- peratures.
Page numbers refer to omrob previous version. Refer to the catalog when ordering. Press the O key for at least three seconds to move from the operation Initial Setting Level level to the initial setting level.
By pressing ‘print’ button you will print only current page. PageStandby sequence reset: No function is assigned to alarm output 3. Section Shifting Input Values Method for a 2-point Use a 2-point input shift if you want to increase the accuracy of the readout Shift values across the range of the sensor. PageScaling upper limit, Scaling lower limit, Decimal point: Refers to control in which the MV is proportional to the deviation control error.
No assignment Control output heat- ing C-O: If the output remains shorted, fire will occur due to overheating of the heater or other cause. Page Note Protection cannot be cleared or changed without the password. To return to the operation level, press the O key for at least one second.
To move to the advanced function setting level and calibration level, you must enter passwords. Communications Function U or D keys. Upper and lower-limit alarm 2: The default is for segment displays. This parameter sets the current for the HS alarm to be output.
Omron E5CN User Manual
For this reason, offset the readout value using a 1-point or 2-point shift as manuql in this section. Doing so may occasionally result in electric shock, fire, or malfunction.
Heater Current 2 Value Monitor Alarm 1 must be assigned. Not doing so may occasionally result in unexpected events. Some parameters are not displayed depending on the protect level setting and the conditions of use. This section describes the parameters set in each Starting in automatic Manual control level level.